On July 1, 2020, we began a new six-month compliance sampling monitoring period in University Park. Compliance samples allow us to measure lead levels in water that has sat stagnant in customers’ pipes for six or more hours and is therefore at a higher risk for lead exposure.
In July 2020, we collected 66 compliance samples from University Park homes and businesses so we could better understand the chemistry in customers’ pipes and track our treatment’s progress.
Moving forward, on an ongoing monthly basis, we will collect additional compliance samples from homes within our existing sampling pool. To keep the public and other stakeholders informed of our progress, all results will be shared on this page by the 10th of each month.
Customers can call 877.987.2782 at any time to request water sampling.
July Data Update
Updated on 08/10/2020
Overall water quality in University Park has improved, but data continue to show that it is critical that impacted customers regularly use their tap water to fully resolve this situation.
About 73 percent of all compliance-sampled homes are at or below the Environmental Protection Agency’s threshold for lead, 15 micrograms per liter (ug/L), as of July 2020.
According to the EPA’s Lead and Copper Rule that regulates drinking water, the treatment is considered effective when 90 percent of sample locations meet the EPA threshold. The data demonstrate that overall lead levels have improved, but elevated lead levels remain in some homes. Lead concentrations continue to show some variability, which is to be expected as the piping continues to adjust to the treatment.
To view a table listing all compliance sample results for each sampled home from the January-July sampling events, please
To help resolve this situation, customers under the advisory should run cold tap water from their kitchen faucets an extra 30 minutes every day, in addition to their regular water use. This will allow us to work together toward the solution and speed up the treatment process.
As illustrated above, using tap water moves the treatment through the system so it can establish a protective layer inside customers’ home plumbing. The protective layer will stop lead inside customers’ internal plumbing from interacting with water flowing into their homes.
In the same way that painting a room at home sometimes requires several coats of paint, the treatment requires more water flow to fully coat the home’s pipes.
By the end of 2019, 100 percent of samples that were collected from University Park homes after running the tap water for two to three minutes had nearly non-detectable lead levels. This validates that, in addition to helping the treatment work, running the tap water is highly effective at reducing potential lead exposure.
We thank our customers for their continued patience and cooperation.
For more information about compliance sampling and our process, as well as our archived data updates, please see below.